This tutorial will help with wiring checks
- Have a power meter check the voltage after writing 50% on the damper cmd within ankalytik connector view.
- If the analog input is not changing check wiring
- Make sure wiring on the actuator is as follows red white blue yellow and on the other side where it connects to the EAC is red blue yellow-white.
T is common
Y is input
U is output 2-10V
Check 10V is being red between T and U when 100% is written from the back-end.